- Keywords: Casualty information, Maritime
Relevant for design offices, shipyards, suppliers, owners/managers and flag states.
Course of events
On a fully loaded container vessel, a fire was detected inside one of the forward cargo holds. Direct access to the fire was impeded due to its location at mid-height in the hold with containers stacked on hatch covers.
Fire-fighting commenced using the water drenching system supplied by the port and starboard fire main lines, connected to nozzles beneath the hatch covers. But this was hampered due to leaking pipe expansion joints, rendering one side out of action.
The CO2 system was engaged, but the line was also found to be leaking at pipe and valve flanges in the CO2 room and in the under deck passageway, preventing total flooding of the hold with CO2.
The crew also attempted to provide additional water via fire hoses through gaps in hatch covers from the main deck. First attempts were hindered, as the fire hose couplings had a different diameter to the hydrant couplings dedicated to the drenching system. However, the crew managed to contain the fire until it was finally extinguished at port. The vessel was detained by the port authorities, and the incident was subject to investigations by several parties, including the flag state.
Extent of damage
The cargo hold transverse bulkhead structures had locally buckled, and nearby electrical fittings were burned. There were no casualties or personal injuries reported.
Several adjacent containers in the cargo hold were damaged by heat, smoke and water. The vessel’s schedule was significantly interrupted, delaying the delivery of high-value goods.
The fire is thought to have started in a container carrying dangerous goods, possibly of an explosive nature. The actual goods were most likely not declared, leading to improper stowage and segregation.
The leaking fire line was probably due to a combination of deficient axial support or stoppers and misaligned pipes outside the coupling manufacturer’s recommended tolerances.
Leakages of CO2 at the flanges of the CO2 pipes and fittings could be the result of poor workmanship and wrong practices during installation. Gaskets of a different pressure rating and multiple gaskets to compensate excessive gaps were also found in several flange joints.
The CO2 line’s remote control valves were dismantled after the incident and found to be contaminated with entrapped water containing foreign particles. The valve adjustment nuts were set, but apparently in a position restricting the maximum flow rate of CO2.
Rules and regulations
The vessel was approved in accordance with applicable classification society rules, and in compliance with relevant regulations under SOLAS, Chapter VII, the IMDG code and MARPOL Annex III at the time of construction.
To provide a standard approach when testing CO2 systems, DNV GL has established its interpretations of SOLAS as presented under section 3.20 in the publication Statutory interpretations — DNVGL-SI-0364 (see Ref.1). These statutory interpretations (SI) also contain other useful guidance on SOLAS-related topics.
As an immediate preventive measure, we recommend to critically review on-board maintenance and inspection programmes concerning fire protection systems and appliances. Necessary amendments identified should be implemented as soon as possible.
Some specific recommendations for the following stakeholders:
- Responsible crew members must be competent and fully acquainted with the operation of all fire-fighting equipment on board each vessel. Training must be followed up on a continuous basis.
- Unlike the active fire-wash deck piping system, fixed CO2 piping systems remain dormant until required, but still need to be checked and maintained. It is essential that a proper maintenance and inspection regime for fixed CO2 fire-extinguishing systems are arranged as recommended in MSC.1/Circ.1318 (see Ref.2) and supplemented by the manufacturer’s instructions. CO2 pipes shall be blown through annually to ensure that they are free from debris and not clogged. Manifold and distribution valves are always to be operational.
- In the statutory interpretation SI-0364 (see Ref.1), it is specified that section (or control) valves be internally inspected at least once every five years, which is in line with MSC.1/Circ.1432 for fixed-gas extinguishing systems. Planned inspections of different valves are advised to be distributed over the five-year period.
Shipyard, design office, supplier
- Procedures for the complete installation, inspection and testing of each type of piping system must be in place, understood and monitored, i.e. coordination needs to be in place between each involved outfitting department for hull, machinery and accommodation. If hydraulic tests are carried out, it is essential that the piping system, including all valves and fittings, are completely cleaned and dried for systems such as CO2.
- Manufacturers’ tolerances and yards’ standards for all fittings, e.g. clamps and expansion couplings, must be readily available, strictly adhered to and properly checked. Typically, a good practice for the control valves would be to seal the spindle at the designated set point after testing.
- The design drawings must reflect all applicable details for each piping system, i.e. capacity of pumps, remote control of valves, arrangement of supports and stoppers, etc. It is essential that signboards, marking and operating instructions are clear and unambiguous.
Other important notes
Due to an increased number of fire incidents on container vessels, DNV GL published an article in its No.1 2016 issue of Container Ship Update (see Ref.3). The article identifies several areas to ensure and improve fire safety on board container ships. A particular concern is the wrong declaration of DG cargo, which has significantly contributed to cases involving fire and explosion. Export and import legislation is outside the scope of ship classification. However, the risks associated with carrying dangerous goods pose a real threat and danger to the vessel and crew. All stakeholders should be aware of freight forwarding procedures and limitations (see Ref.4).
Email us at Fire Safety & Life-Saving
Latest Technical and Regulatory News
20 December 2018 | Statutory | NEWSThe EU ship recycling regulation - coming into general application on 31 December 2018The EU Ship Recycling Regulation (EU SRR) is coming into general application on 31 December 2018. Additional requirements are imposed to any new EU-flagged vessel and vessels under EU-flag going for recycling. These measures are subject to PSC and flag state inspections effective from 2019. This statutory news provides you with a summary of the EU SRR (1257/2013) and recommendations of how to manage the Inventory of Hazardous Materials (IHM) process.
18 December 2018 | Statutory | NEWSUpdate on emissions to air regulations for ships operating in Chinese coastal watersThis statutory news covers vital information from the Chinese Ministry of Transport: introduction of a 0.5% sulphur limit for ships entering China’s coastal waters, and updated NOx regulations for imported ships engaged in domestic trade. Both regulations will enter into force on 1 January 2019.
10 December 2018 | Statutory | NEWSMake sure you comply with IMO DCS – Deadline 1 January 2019With three weeks to go before IMO’s fuel data collection system (DCS) starts on 1 January 2019, many companies still have not submitted their SEEMP Part II fuel oil consumption data collection plan for approval. This statutory news contains some last-minute recommendations.
10 December 2018 | Statutory | NEWSMARPOL Annex VI update in force from 1 January 2019 on NOx, BDN, Ship implementation planNew MARPOL amendments adopted by Resolution MEPC.286(71) include two new emission control areas (ECAs) for NOx, and amend the information to be included in the bunker delivery note (BDN). In addition, a new IMO circular has been issued with guidance for making a ship-specific implementation plan. More in this statutory news.